This category includes doors evaluated without an edge-sealing system between the door
and frame. It also includes doors evaluated with a sealing system incorporated (concealed
or visible) into the edge of the door by the licensed manufacturer or machining distributor.
Meeting edges of pairs may require an astragal or an edge-sealing system. Please refer to
individual door listing.
This category includes doors evaluated with an edge-sealing system (Category G) field-applied
to the labeled frame or door. The application of the edge-sealing system does
not require any machining of the frame or door. Please refer to Category G, "Edge-Sealing
Systems" for individual manufacturer's listing.
These assemblies are eligible for use in any Category C, "Standard" frame. These doors may also
be installed in frames listed in Category C, "Proprietary" in accordance with the frame manufacturer's
All doors listed in Category B are eligible to bear the "S" (for Smoke & Draft Control assemblies) if a
listed Category H, "Smoke & Draft Control Gasket" has been applied to the assembly. Please refer to
Category H for individual gasket manufacturer's listings.
This category includes frames not based on ANSI-A155.1/UL-63 construction type (such as aluminum, wood,
light gauge steel, composite, etc.). These listings will reference specific door types for which each
frame is qualified. All frames listed in this section may be used in positive pressure assemblies per the
terms and limitations of the individual listing.
This category includes frames based on ANSI-A155.1/UL-63 and includes sidelight/transom assemblies. These
frames are qualified for use in positive pressure assemblies, with Category A doors, or with Category B doors
utilizing Category G, "Edge-Sealing Systems". These frames, when installed in pairs in drywall construction,
shall have anchors installed in the head section, minimum 24" O.C. These listings will not reference specific
door types, as all door types are eligible.
This category includes doors and frames that are labeled for positive pressure compliance as an assembly.
Refer to ITS "Directory of Listed Building Products" for hardware listings. Hardware that qualifies for positive
pressure will be noted with the statement "Also conforms to UBC-7-2-97/UL-10C".
Products listed in this category have been evaluated for use in positive pressure fire door assemblies for
specific types of doors and with specific glazing systems. Refer to the individual listings for limitations
This category includes field-applied systems only. Category G, "Edge-Seal Systems" are for use on Category B
doors, or meeting edges (only) of Category A doors. These systems are surface-applied to either the perimeter
of the door or frame, or meeting edge of the door. They may be kerf-applied, adhesive-backed, or mechanically
This category includes gasket systems that are surface-applied (such as kerf-applied, adhesive-backed, or
mechanically-attached) to frames or doors. It includes gasketing for the meeting edges for use in pair and
double egress assemblies.
Note: This category covers gasket systems that have been evaluated for use in positive
pressure rated assemblies, but do not provide an edge-sealing system to the opening (see Category G).
These gasket systems have been evaluated in accordance with UBC-7-2-97, Parts I and II.
Note: This category covers gasket systems